AQUALIS – CALEO MICROCONNECT N B Installation Fonctionnement Mise en service Maintenance Installation Operation Commissioning Maintenance. Aqualis Caleo. 60H. 60HT. 70HT. Heating capacity *. kW. Power input *. kW. COP. Refrigerant fluid RC – Load. CIA. T CALEO. 10 – NA E. Instruction manual . The TDC series AQUACIAT CALEO heat pumps meet the heating needs of 0 = Aqualis Caleo.
|Genre:||Health and Food|
|Published (Last):||9 October 2008|
|PDF File Size:||10.49 Mb|
|ePub File Size:||7.46 Mb|
|Price:||Free* [*Free Regsitration Required]|
Terminal display when the outdoor temperature is less than P9 and only the boiler is authorised. Multi Split Units If there is a fault on any LG Multi aqualid, an Error mark is indicated on the display window of the indoor unit, wired-remote controller, and LED s of outdoor unit control board.
Then check for any leaks.
Please read before installation More information. In hot water production mode heating, pool, frost protection or domestic hot aquais modes: AWG 16 to 28; or 0. Failure to comply with the requirements of the above standards will void the CIAT warranty.
Power Type Battery power. Minutes advance quickly when pressed and held.
D e u t s ch Connection diagrams schematic diagrams Page 10 5 Troubleshooting Page More information. Commissioning includes making the electrical More information. The valve does not need to be separated from the heater by a shut-off valve. Protect from prevailing winds. Please contact your boiler manufacturer to find out whether the heating source aquapis compatible with Microconnect control.
Remove the top as shown in Figure 1 and make a connection to terminal block J1 on the PSU board the one cale the contactor.
Washing the system with a suitable cleaner is recommended the type of cleaner depends on the system s materials. L Always top up with the same type of mix initially used. The recommendations and aquualis given in the maintenance instructions and the special instructions on the labels must be followed. Failure to follow the safety rules and other basic safety precautions may result in serious More information.
NAN – CIAT – PDF Catalogs | Technical Documentation
Please read carefully More information. Common demands for Category 2 and 3 installations Although it is rain resistant, it may be installed under a shelter with adequate ventilation on all four sides. Terminal display when the outdoor temperature is less than P9 and only the boiler is authorised. Please read cqleo installation.
Air/water heat pump – AQUALIS R series – CIAT
Fault management remains on during test mode. Each comes equipped as standard with: To do so, first insert the tabs Fig.
Specifications – Settings stored in memory for two hours following a power cut – Blue backlit digital display – Maximum dimensions: Check for any loose electrical connections. To do so, loosen the screw Fig.
Do not use products made with monoethylene glycol, which is toxic. Clean the drain pan.
Commissioning includes making the electrical. This can be done by opening the manual bleed valve located under the unit cover when turning the unit on or by installing daleo section of the water line and an automatic bleed valve over the unit. Access to level-1 customer settings Indicator 0: These instructions covers the installation of replacement coil kit into.
Page 2 Compressor More information. It is not necessary to add glycol to your system if you are absolutely sure that there is no risk of freezing temperatures in awualis area. You may use refrigerants made with monopropylene glycol or a natural compound containing one or more corrosion inhibitors never use monopropylene glycol by itself; always mix it with corrosion inhibitors.
Always disconnect the unit before attempting to wire connections. Connection – Attach the two wires to the terminal Fig.